12 New Old School 3, Switch Wiring Solutions
Related photos in this diagram:
Other recommended diagram ideas:
New Old School 3, Switch Wiring Solutions - "what is commonplace within the diagrams above and with any three-manner switch circuit is that the power warm wire entering the circuit will continually go to the commonplace terminal of the primary switch. The hot wire from mild always is going to the common terminal of the second one transfer. The tourist wires cross from transfer to interchange linked to the vacationer terminals, it does not be counted which. So long as you preserve this in mind, a three-manner circuit becomes simply simplified. And of direction the impartial will constantly cross immediately to the weight.".
Edit i see your extended diagram explains the kitchen mild transfer turned into no longer a dead short however simply strength to the switch. You had the white marked black however have corrected that during your ultimate drawing. Using purple for the switched power and travelers is the better technique as others talked about. Your final drawing looks electrically sound. With your current wiring it isn't always feasible, but the nec requires a neutral at transfer places with a few exceptions. In case you are not being inspected you could don't forget this 'grandfathered' wiring. Inside the destiny, you have to take a impartial to the transfer vicinity.
One way to moot the complete rely is cross new-tech. Set up the appropriate model of "smart transfer" inside the 2-gang box and a associate faraway transfer in the remote container. Re-challenge the white, black and/or crimson as needed by the companion remote.
The ceiling field at the left is how i think it ought to be wired, with one exception. Be aware that there may be black tape proven at the impartial going to the sink light transfer. This transfer isn't always a three-manner switch so i think that the black tape is a mistake. The recent from the ceiling field goes to the switch which then sends it to the light fixture. The neutral from the light fixture ought to hook up with the neutral from the ceiling container inside the switch box and all the neutrals are connected together inside the ceiling box as proven.