# 6 Simple 6 Gauge Wire, Rating Nec Ideas

## Other recommended diagram ideas:

Simple 6 Gauge Wire, Rating Nec Ideas - Exception: wherein one-of-a-kind ampacities follow to adjoining quantities of a circuit, the better ampacity shall be approved to be used beyond the point of transition, a distance equal to three.Zero m (10 feet.) Or 10 percent of the circuit duration figured at the better ampacity, whichever is much less.

However, if the 1/zero, xhhw se cable with al conductors is installed in thermal insulation in an attic wherein the temperature is one hundred ten˚f, then the 90˚c column of desk 310.15(b)(sixteen) can be used to accurate for the better temperature. The correction element for a hundred and ten˚c ambient temperature is .87 and the ampacity of a 1/zero xhhw from the 90˚c column of table 310.15(b)(16) is one hundred thirty five amps.? so a 1/0 xhhw al conductor can deliver one hundred thirty five amps x .87 = 117 amps.? this value of 117 amps needs to be compared with the rating from the 60˚c column because the cable is installed in thermal insulation.? the ampacity from the 60˚c column is simplest a hundred amps, so this is the most permitted load on a 1/0 xhhw al conductor mounted in thermal insulation.

Properly sizing an se cable hooked up in thermal insulation requires a cautious examination of the code. Section 338.10(b)(four)(a) is all approximately indoors installations of se cables and states: where established in thermal insulation the ampacity will be according with the 60°c (140°f) conductor temperature rating. The maximum conductor temperature score shall be approved for use for ampacity adjustment and correction functions, if the final derated ampacity does not exceed that for a 60°c (one hundred forty°f) rated conductor.