13 Cleaver 220V Baseboard Heater Wiring Diagram Photos
Related photos in this diagram:
Other recommended diagram ideas:
Wiring Diagram, Electric Baseboard Heater With Thermostat, – Baseboard Heater Wiring Diagram 240V - Call is ***** ***** i could be happy to assist you along with your electrical query. My purpose is to exceed your expectancies on simply solution! 1) baseboard warmers need to be stressed out in parallel with every collectively and then linked to the tstat. The l1 & l2 connection are the line facet connections and those are the two wires that originate from the breaker. The t1 & t2 are the two wires that extend out to the paralleled heater wiring (load aspect connection). 2) test the diagram proven below. Is that this how you have related the wires? Since you are the usage of black and red wires, my diagram indicates white and black, however the identical principle, just a distinct color. Pink and black can be used in my diagram. Simply substitute the white for a crimson. 3) what cord shades land on the double pole breaker? Black & purple or black & white? Four) 12/3 isn't required as you may have used 12/2 romex. A 240 volt baseboard heater simplest requires 2 warm conductors. Just cap off the white wires at each ends if you are the usage of black/purple. !.
The number of heaters that you could appropriately cord to one thermostat will depend upon the dimensions of your breaker in the electrical box, what sort of wiring you are using and the wattage of the man or woman heaters.
Good enough, that is flawlessly suited and is not any trouble. The white and black that land at the breaker are the tstat l1 & l2 connections (line aspect of the tstat). At the tstat container, just use a 6" (6 inch) pigtail of 12 awg white wire and integrate to the two white load side wires to (1) one 6" white cord and terminate to the t1 or t2 termination (load aspect warmers) at the stat. Repeat the same pigtail system for the two black heater wires and connect to the t1 or t2 termination on the stat (load aspect connection). Use one 6" black 12 awg for this pigtail. You ran the two heater cables as "domestic run" to the stat which is exceptional as that is additionally a parallel connection. The other alternative as shown in my diagram is to daisy chain the two heaters together which is also a parallel connection. Each wiring strategies are good enough. Your wiring parallels the warmers on the stat, my diagram parallels the wires at the warmers.